Ballast - Universal Lighting Technologies Inc. - Facility Management Product Release
The B232PUS50-A Ballastar light-level switching ballast for T8 lamps provides light level control by switching from full light to 50-percent power using standard wall switches or relays. This allows for compliance with ASHRAE 90.1 and California Title 24 switching requirements. Light-level switching maintains even illumination of the luminaire.
It incorporates two hot power leads for control with two standard switches or relays. Switching one lead on provides 50-percent power while having both switches on provides 100-percent power.
It is designed to operate one or two F32T8, F25T8, or F17T8 lamps. Full light ballast factor is .88. It complies with ANSI ballast requirements and includes end-of-lamp-life shutdown circuitry with auto re-strike for safe operation. Universal input voltage allows for this ballast to be connected to any voltage from 120 to 277 volts at 50 or 60 hertz.
- Daylighting Advantages And Disadvantages
- EPAct 2005: The Energy Policy Act of 2005 Explained
- Fluorescent Lamp Disposal: What Are The Options?
- Getting Started With Lighting Occupancy Sensors
- T5 vs. Metal Halide: Finding The Energy Savings
- The T8 Ballast: Not Every Ballast Is Created Equal
- Buyer Beware: Practical Tips for Germicidal Lighting Use
- What to Know about Germicidal Lighting and Coronavirus
- Tunable White LED Lighting: Questions and Considerations
- 5 Ways to Avoid Flicker in LED Lighting Installations
- Advances in LEDs Bring Architectural Performance to Commercial Products
- AMA: Some Street Lighting LED Options Hazardous to Health