Best Information Tool For Busy FMs
We will keep you updated with trends, education, strategies, insights & benchmarks to help drive your career & project success.
- Building Automation
- Ceilings, Furniture & Walls
- Doors & Hardware
- Equipment Rental & Tools
- Energy Efficiency
- Facilities Management
- Grounds Management
- Fire Safety/Protection
- Maintenance & Operations
- Plumbing & Restrooms
- Power & Communication
Lighting Panels - Square D - Facility Management Product Release
Clipsal Area Lighting Panels provide a simple way to realize daylight harvesting schemes in an individual conference room or suite within a commercial building. They are designed to meet energy code requirements related to reduction in lighting loads by integrating natural light with artificial light. Panels can be set up as a stand-alone system or connected as a part of a larger Square D Clipsal network. A simple Cat-5 cable connection gives the pre-engineered enclosed panels the ability to integrate light-level detection, occupancy detection, keypads and switching.
Panels automatically dim lights to capitalize on available natural light, and automatically turn lights off after room is empty. Various pre-programmed lighting scenes can be automatically executed by the panel by pressing a button on a lighting control keypad.
Power is distributed to the panel from a single home-run connection to the power source. Panels consist of a NEMA 1 enclosure with Clipsal DIN rail-mounted, microprocessor-based output modules. Several options are available, including a four-channel relay output package, an eight-channel relay output package, and four-channel relay and four-channel 0-10V dimming packages. Relay models have four or eight robust 20A relay outputs and are available in both 120V and 277V. Dimming models are available in both 120V and 277V and include four 20A relay outputs and four 0-10V outputs for control of dimmable fluorescent ballasts. All Area Lighting Panel configurations are available with a power supply, which provides extra power to the network when multiple keypads or sensors are required.
- Daylighting Advantages And Disadvantages
- EPAct 2005: The Energy Policy Act of 2005 Explained
- Fluorescent Lamp Disposal: What Are The Options?
- Getting Started With Lighting Occupancy Sensors
- T5 vs. Metal Halide: Finding The Energy Savings
- The T8 Ballast: Not Every Ballast Is Created Equal
- Effective Project Management Helps University Reduce Energy Usage
- Manager's Role in Project Management Leads to Successful Renovations
- How Lighting Energy Efficiency Connects to Wellness
- 5 Ways to Avoid Flicker in LED Lighting Installations
- Advances in LEDs Bring Architectural Performance to Commercial Products
- AMA: Some Street Lighting LED Options Hazardous to Health