- Building Assistant »
- Facility Manager at Colorado Nonprofit! »
- Assoc/Senior Eng (5-yr limited term) »
- Facilities Maintenance Supervisor »
- Custodial Assistant »
Sprinkler System Offers Increased Fire Suppression
Viking Corporation has announced that its K28 ESFR sprinkler is now FM Approved to protect high-piled storage up to 50 ft (15,2 m) in storage facilities with ceilings as high as 55 ft (16,7 m), without requiring an in-rack sprinkler system. As a result, the Model VK514 pendent sprinkler can significantly reduce installation and maintenance costs while increasing racking flexibility in warehouses as high as 55 ft (16,7 m).
The new FM Approval is offered in addition to the sprinkler’s existing UL Listing, which provides ceiling- only sprinkler protection in warehouses up to 48 ft (14,6 m) in height. The FM Approval classifies the Model VK514 as a Quick Response Storage sprinkler, approved to protect Class 1-4 commodities and Group A, cartoned unexpanded plastics. The FM design specifies a design pressure of 80 psi (5,5 bar) with a remote area consisting of nine sprinklers, installed with three sprinklers on three adjacent branch lines. The K28 ESFR sprinkler is available in both ordinary and intermediate temperature ratings – 165°F (74°C) and 205°F (96°C) – and with a 1” NPT or 25mm BSP thread size.