view all Case Studies
August 23, 2017 -
Harvard had just installed a new 8,500 CFM air handling unit that was meant to supply heat to Girguis Lab and an adjacent facility. When the unit was brought online, however, its fan was operating at around 97 percent of capacity with little effect — and that was even before the system was connected to the adjacent facility. It was determined that leaks in the ductwork were reducing static pressure to such a degree that air couldn’t reach its destinations. With ducts hidden under insulation and behind layers of pipes, fixing those leaks seemed an impossible task.
Fortunately, a new approach to duct sealing called Aeroseal works from the inside of the air shafts to locate and seal leaks. In the Aeroseal process, a non-toxic aerosol-mist of sealant is blown throughout the interior of the ductwork. The microscopic particles of sealant remain suspended in air until they reach a leak. There, they cling to the edge of the hole and then to other sealant particles until the leak is completely sealed.
The technology was developed at Lawrence Berkeley National Laboratory in 1994, with research partially funded by the U.S. Department of Energy. It has proven to be 95 percent effective at sealing air duct leaks.
In just a matter of days, the problem was fixed. Sealing quickly reduced the system’s duct leaks from more than 5,800 CFM down to 429 CFM — a 98 percent reduction. After duct-sealing, the fan operated at only 37 percent of capacity. The system was quieter, and university engineers were relieved.
"I would absolutely call this a project saver,” says John Hollister, senior capital project manager at Harvard. “Our only other option was to tear down walls and demolish the building structure in order to access the leaky ductwork. We were very pleased with the results and I honestly don’t know how we would have solved this issue if the Aeroseal technology wasn’t available.”
When switching its lighting system from fluorescent to LED, one Houston-area school district had three goals in mind: save money, save energy and create a better learning environment. With the help of a local lighting manufacturer, that school district is now projected to save hundreds of thousands of dollars, dramatically lower environmentally harmful emissions and, most importantly, give students, faculty, and staff an environment where they will be more alert and be able to concentrate easier.
The case study discusses how ABM was able to help Madison County Schools garner over $12 million in guaranteed energy and operations savings while keeping expenses budget neutral.