Data Issues Are Critical With Fault Detection And Diagnostics (FDD)
December 2, 2013 - Contact FacilitiesNet Editorial Staff »
Today's tip from Building Operating Management comes from Jim Sinopoli of Smart Buildings LLC. Facility managers who are considering fault detection and diagnostics tools should be aware of the importance of data and network issues. Here are some points to keep in mind.
Lack of Data. Fault detection and diagnostics tools rely on data from building automation systems. If there are not enough sensors, if the sensors are inaccurate, or if the building has a legacy control system and for some reason accessing the BMS database or controllers is difficult, there can be issues with obtaining the accurate data required.
Using the Diagnostic Data. Many of the fault detection and diagnostics software tools can provide information to the technician or engineer regarding potential corrective actions. This information needs to be integrated into the work order system, which may be one application in a whole suite of facility management applications, in order to use the information effectively.
Applications in the Cloud. Many companies offering fault detection and diagnostics software will provide the application on the client site, but have an option to provide the application as "software as a service" (SaaS) or in "the cloud." Essentially the vendor hosts the application, and the facility manager accesses the application through a normal web browser. This can be an issue with many corporate IT departments because of the need to pierce the corporate IT firewalls and security to get to the BAS data the application needs.
Prognostics Data. While fault detection and diagnostics tools seem inherently capable of providing prognostic data — that is, it can analyze fault conditions or degradation faults and predict when a component will fail or not be able to perform correctly — very little has been developed in this area. In addition, prognostic data would allow for more proactive, condition-based maintenance, which would be a different approach for facility management organizations that are reactive and corrective.