Part 1: Four HVAC Gains With No Budget Pains
Four HVAC Gains With No Budget Pains
By James Newman - January 2012 - HVAC
It's hardly news that buildings use 40 percent of the natural resources and more than 70 percent of the electrical energy in the United States. And facility managers know there are plenty of ways to get buildings to use less energy — measures that send savings directly to the bottom line. By now, most facility managers have replaced T12 lamps with electronic ballast and T8s, or even more efficient lamps. Many have installed motion sensors. If the lighting retrofit was good enough, the organization might have received a tax deduction of $0.60 per square foot under the Energy Policy Act of 2005 (EPAct 2005).
But what about the "heart and lungs" of a building: the HVAC system? The thermal energy plant and HVAC systems can go from "green" to "gray" in a very short time after they have been installed or retro-commissioned. Nevertheless, implementing HVAC upgrades is far from easy in many organizations. Companies put off having an energy audit by an outside team because they don't want to spend the money on what the recommendations in the audit might cost.
Fortunately, there are many ways to improve HVAC performance that do not cost a lot of money to implement. Some have more to do with the manner in which the building is operated than the actual HVAC system itself. Most low- and no-cost items fall into four categories:
- Equipment Scheduling. HVAC equipment running when not required is a major source of energy waste. HVAC equipment running when it's not needed, along with plug loads for chargers, computers, copiers and printers, task lights and other items that are on when not necessary, can account for as much as 10 percent of electricity use. Chargers typically use more energy when left plugged in 24/7 than the equipment they charge.
- Sensor Error. Sensors are seldom calibrated after installation, yet over time they drift from their setpoints. Or use of the area has changed but location of the sensor or its setpoint has not.
- Simultaneous Heating and Cooling. To make working spaces more comfortable, many older HVAC systems use some form of reheat. That in itself is an energy hog, but if the cooling and heating setpoints are incorrect, more energy will be used than is necessary.
- Outdoor Air. The amount of outdoor air brought into a building to provide proper indoor air quality (IAQ), usually mandated by code, is a function of the number of people, area of the space and type of work. Issues like outside air dampers that are stuck in the open position or artificially held open (or closed), sensors that aren't working properly — or are incorrectly wired to the return and the outside air damper so that the damper is wide open, instead of being at minimum position during extremes of hot or cold temperatures — contribute probably more than almost anything to increased energy use, as well as potential comfort problems.
There are many ways to reduce energy costs by addressing these four areas without spending a lot of money.
1. Equipment Scheduling
HVAC equipment often operates during hours it is supposed to be off, even though the building automation system says it is off. Checking the BAS to make sure it is operating properly does not take an extraordinary amount of time but can save an extraordinary amount of money.
Don't stop with HVAC if the goal is to find low-cost ways to reduce energy use. Put plug loads on a power strip that sits on people's desks and teaching them to turn off the toggle switch when they leave at night. There are also power strips that automatically turn off after a period of time where there's been no load. Of course, occupants must be taught to save the work on their computers before they leave their desks. Education of occupants is an important part of a successful energy program, as is getting buy-in before the program begins and consulting them throughout the planning process.