- Building Technician »
- Director of Facilities - SFPL »
- Plumber, Facility Operations, Bethesda East »
- Groundskeeper »
- Mechanic, Facility Operations, Bethesda East »
Cost Of Replacing Obsolete Equipment Can Help Sell HVAC Upgrade
December 17, 2014 - Contact FacilitiesNet Editorial Staff »
A deferred capital renewal (the cost to replace a unit in kind if the unit is beyond its useful life) analysis can help justify large HVAC and other projects. Consider the replacement of a 30-year-old water chiller. Typically, chillers installed at this time were constant speed units. Based upon ASHRAE numbers, the average service life of a water-cooled chiller is 23 years. That does not mean that, once a chiller has been in service for 23 years, the unit will fail, but rather that a plan for the chiller replacement should be in place based on that average service life. A 450-ton constant speed water-cooled chiller has been designed to have a chiller efficiency of 0.70 kW/ton, but because of the age of the equipment the chiller could be de-rated to an efficiency of 0.81 kW/ton, assuming a 0.5 percent per year degradation. A variable flow chiller unit can be selected to operate with an efficiency of 0.50 kW/ton. Based upon the unit operating at full load condition for 1,500 hours and an electric rate of $0.08/kWh, the annual savings for installing the VFD unit is approximately $16,700 per year.
The cost for the new VFD chiller system is estimated to be $250,000. This would correspond to a simple payback of close to 15 years. If the analysis included the cost to replace the unit with a constant speed chiller (assuming the cost of $203,000), the difference in capital costs is only $47,000 and the simple payback would be reduced to 2.8 years. Even if the analysis assumed that the constant speed chiller was installed with the original efficiency (0.70 kW/ton) the simple payback is still 4.3 years. Very careful calculations are required to ensure that deferred capital calculations are accurate.
It is difficult to identify the deferred capital savings in terms of simple payback when evaluating equipment that still has useful remaining life. The cost to replace the equipment cannot be simply subtracted from the cost of the energy conservation measure. However, a complete life cycle cost analysis can be completed to identify the most economical approach.
This brief came from Andy Jones, mechanical engineer/project manager at RMF Engineering.
Read the full story.