- Mechanic, Facility Operations, Bethesda East »
- Groundskeeper »
- Manager Plant Operations, Facility Operations »
- Space Management Specialist »
- Plumber, Facility Operations, Bethesda East »
A VFD Offers Energy Savings, Other Benefits from Part-Load HVAC Operation
July 1, 2011 - Contact FacilitiesNet Editorial Staff »
Today’s tip comes from James Piper, contributing editor for Building Operating Management: Variable frequency drives, or VFDs, offer multiple benefits for HVAC systems.
For more than 20 years, VFDs have successfully been installed on fan and pump motors in wide range of variable load applications. The most significant benefit of the use of a VFD is energy savings. By matching system capacity to the actual load throughout the entire year, major savings in system motor energy use is achieved.
Another benefit of the units is reduced wear and tear on the motors. When an induction motor is started, it draws a much higher current than during normal operation. This inrush current can be three to ten times the full-load operating current for the motor, generating both heat and stress in the motor’s windings and other components. For motors that start and stop frequently, the heat and other stresses produced contribute to early motor failures.
In contrast, when a motor connected to a VFD is started, the VFD applies a very low frequency and low voltage to the motor. Both are gradually ramped up at a controlled rate to normal operating conditions. With no significant inrush current, heating and stresses are practically eliminated, extending motor life.
VFDs also provide more precise levels of control of applications. For example, high rise buildings use a booster pump system on the domestic water supply to maintain adequate water pressure at all levels within the building. Conventional pump controls in this type of application can maintain the pressure within a certain range, but a VFD based system can maintain more precise control over a wider range of flow rates, while reducing energy requirements and pump wear.