New Content Updates
Educational Webcast Alerts
Building Products/Technology Notices
Access Exclusive Member Content
By Lindsay Audin
Lighting Article Use Policy
In the past, daylighting controls got mixed reviews, with many lighting maintenance contractors complaining that such systems might be disconnected within a year due to occupant complaints. Changes to both design and cost are now making application of that option less complicated and more productive. While early systems included only indoor light sensors for controlling fixture output, today's designs include outdoor sensors (and appropriate control software) that avoid changes in lighting output due, for example, to a passing cloud. Greater compatibility among sensors, dimmers and dimming ballasts has addressed issues with linearity in control.
A drop in the cost of dimming ballasts (to as low as about $30) has also helped, with remotely controlled units offering a variety of cost-cutting options.
Occupancy sensors once had a checkered reputation, with occupants occasionally needing to wave their arms to keep lights on. To respond to such issues, today's sensors have built-in "learning" capability that resets sensitivity (and perhaps cycle time) so they are more occupant-friendly. To increase savings and occupant control, vacancy sensors (which are manually turned on rather than coming on when one enters a room) are now available from many manufacturers. Such units greatly reduce false activation as people pass by a doorway, and leave lights off unless an occupant wants them on. Some sensors are also wireless, allowing ceiling units to be easily installed (and moved) as space use and layouts change.
Many fixtures (including LED, fluorescent and HID) may now be purchased with controls integrated into them. Both occupancy and lighting sensors are available. Such units may be most appropriate in stairwells, hallways and warehouse lanes where views are not blocked by partitions or other obstructions. Stairwell units are designed to step-dim (not shut off) lighting to ensure safety and security at all times. Where stairwells are rarely used, major savings (over 70 percent) have occurred. Some decorative and spot/track LED lighting units with manually adjustable dimming levels allow up to 10 settings to allow precise (and changeable) brightness on subjects, with savings proportional to dimming levels.
In atria and on top floors, dimmable skylights are now available from several sources. When combined with daylighting controls, flexibility is enhanced. Tubular skylights with controllable dampers adjust incoming light to improve quality and distribution and to control glare. Larger linear skylights, equipped with rotating baffles, perform similar functions.
Lighting Controls Can Amplify Effect Of More Efficient Light Sources
Daylighting Controls Are Becoming Less Complicated, More Productive
Outdoor Lighting Can Be Managed By Lighting Controls