- Construction engineer, U.S. Dept. of State »
- Operating Engineer »
- Foreign Service Facility Manager »
- Facilities Utility Specialist »
New Generation of LEDs Make Good Case for Retrofit
September 9, 2015 - Contact FacilitiesNet Editorial Staff »
The biggest development in the last decade of lighting has been white LED lamps. Several thousand solid-state lighting (SSL) products using white LED lamps are now available to fit almost any socket. Pricing continues to drop, even as efficiency and quality continue to rise.
Unlike their CFL predecessors, screw-in LED units come to full brightness immediately, maintain light output for decades instead of years, are happy being cycled thousands of times, and love cold environments, all while cutting wattage by 20 to 40 percent (60 to 80 percent when compared to incandescents).
In many cases, power quality and color rendering are also better, mercury is no longer an issue, and fragility is a thing of the past. Color temperature and beam spread options exist to satisfy even lovers of incandescents. Infrared and ultraviolet emissions are so low that museums are switching to them.
The same attributes apply to most LED replacements for tubular fluorescents. Care is needed with regard to maintaining similar light distribution, color temperature, and glare control. Some retrofit kits or replacement lamps may compromise a fixture's UL listing, but many are available that do not do so. While most presently involve ballast disconnection and minor fixture re-wiring, some replacement LED tubes are designed to work with existing electronic ballasts.
Not only does SSL offer additional savings but — unlike all earlier options — it offers the ability to "tune" color temperature. Some LED systems are designed to change it across time to mimic daylight, which might be desirable for its positive human health effects, and productivity.
The fluorescent lighting industry has responded to the SSL challenge, offering T8 lamps that last more than 50,000 hours, with wattages (for a 4-foot lamp) as low as 25 (instead of the standard 32), emitting only slightly fewer lumens. Electronic ballasts with a wide range of ballast factors (BF) are available that offer higher or lower light output commensurate with their wattage. Some high-performance two-lamp units with standard BFs save about 5 watts. When combined with appropriate lamps, a room's light level may be altered by about 35 percent merely by changing lamps and ballasts. Doing so may, at low cost, adjust lighting to accommodate changes in tasks while keeping the same fixtures and layout.
To learn more about the possibilities available with lamp retrofits, read this