- ELECTRICIAN »
- Construction engineer, U.S. Dept. of State »
- Senior Director of Facilities »
- Director of Facilities and Fleet Management »
- Facilities Director »
Minimize Fire Protection Costs Through Design
January 21, 2014 - Contact FacilitiesNet Editorial Staff »
Fire protection system costs can be minimized through careful evaluation of the needs of the space and considerations for how the space can be altered to facilitate fire safety instead of making the fire protection system compensate for the space.
To start with, flammable materials will clearly need adequate fire protection, but how these materials are stored can impact what kind of system is required. Facility managers might be able to avoid the expense of installing a fire pump to provide adequate water to the fire suppression system by exploring options in hazardous or flammable product storage. This might be achieved by reducing hazard heights, using different racking or storage arrangements, or using fire barriers to compartmentalize the storage area, says Tony Schoenecker, senior fire protection engineer for Burns & McDonnell, in the January issue of Building Operating Management. Exploring the options might decrease the fire suppression system's water needs down to where a fire pump would not be needed.
Another way to avoid additional cost by modifying design is in canopies. If the canopies will require sprinkler protection, consider shortening the canopy to within the range of standard or extended coverage dry sidewall sprinklers off the wet-pipe system. This will avoid a dry-pipe system, with its separate sprinkler riser, air compressor and additional maintenance costs.
In buildings where there are different occupancies between floors, a built in fire safety advantage might lie in the concrete deck. A two- or three-inch concrete floor might provide the required fire resistance to the ceiling of the floor below. This might affect how much, or if, sprayed-on fireproofing will be required to the underside of the deck.
Read the article here.