4 tips on boilers
1. Boilers: Four Factors Shape Decision to Repair or Replace
Today's tip from Building Operating Management comes from James Piper, contributing editor for Building Operating Management and Maintenance Solutions magazines. Four factors can help a facility manager decide to repair or replace a boiler.
As with all building components, boilers have finite service lives. Even with ideal maintenance, they eventually require replacement. While a boiler's age is a major factor in determining whether to repair or replace a unit, it is not the only factor facility managers must consider.
No hard and fast rules exist for making this decision, but facility managers need to consider several important factors:
Age. As boilers age, maintenance costs gradually rise. Unless something serious goes wrong, replacement costs will always exceed repair costs. But the trend in maintenance costs is a more important factor. If these costs remain relatively constant, then repairing the boiler most likely is the better option. Consistently and rapidly increasing costs point toward replacement, as does difficulty in obtaining replacement parts.
History. Identical boilers operating in similar facilities often have widely different operating histories. Differences in set-up, operating practices, and maintenance often cause these variations. Operators and managers need to review the boiler's history to see if factors exist that suggest replacement is the better option.
Efficiency. New-generation boilers offer major increases in annual operating efficiency compared to boilers that are only 10 years old. Facility managers should consider the annual savings from replacement when evaluating options.
Configuration. Older systems with central boilers tended to include only one or two large boilers. That set-up often made it necessary to cycle one boiler to match part-load operating conditions. New-generation, centralized systems use several smaller, modular boilers, which allows operators to better match system capacity to facility needs, thus improving operating efficiency. Facility managers should review the historical building loads to see if a cost benefit exists for replacement with modular boilers.
This has been a Building Operating Management Tip of the Day. Thanks for listening.
2. Planning Pointers for Successful HVAC Retrofits
I'm Dan Hounsell, editor of Maintenance Solutions magazine. Today's topic is, planning for successful HVAC retrofits.
It is unusual for a retrofit project in an institutional or commercial facility to go off without a hitch. Schedules, equipment, materials, technicians and a host of other factors need to mesh almost precisely for that to occur. So when the project in question is the replacement of a major HVAC component that just happens to be embedded deep within a facility, success often is even more elusive.
That scenario is exactly what happened when St. Mary's Hospital in Madison, Wis., replaced its 25-year-old boiler in 2007. The project is a prime example of the role planning and preparation play in any project's success.
"I think it's a testament to the planning that we really didn't have surprises," says John Puckett, the hospital's director of plant services. "It was well thought out, well coordinated, well communicated. The staff was able to keep things running. We had contingency plans, but we didn't have to exercise them with the installation of the new boiler."
The department's role in the project went beyond technical issues.
Says Puckett, "Besides developing a close working relation with our contractor partners, communication strategies between the engineers and the staff, as well as our customers — those were the key elements of this department's role. We also had to maintain a consistent and reliable supply of all the associated systems and functions during the installation."
The old boiler's location deep inside the building created a host of challenges related to disconnecting and moving it to make way for the new boiler. That move took an entire week. Ensuring the hospital's utilities remained functional during the replacement process also created challenges.
Says Greg Hatzinger, the hospital's power plant supervisor, "It was a daily challenge, just simply because of where the boiler was located, just to keep services running and relocate feedwater and fuel lines — it was quite a challenge. It took a lot of coordination with the contractors to keep those going."
3. Three Boiler Control Upgrades Can Improve Energy Efficiency
Today's tip comes from James Piper, contributing editor for Building Operating Management and Maintenance Solutions magazines:
When specifying boiler controls it is important to understand that operating efficiency is only one consideration. The boiler control system must be able to meet the facility's peak heating load while operating efficiently under part-load conditions. Typical controls that facility managers should consider when upgrading existing boilers include the following:
1. Flue-gas trim. One of the best indicators of a boiler's combustion efficiency is the flue-gas composition. Trim controls constantly monitor the temperature and the chemical composition of the flue gas, making changes to the combustion controls to limit the quantity of excess air brought into the boiler. While all boilers require some excess air for complete combustion, natural-gas-fired boilers can operate effectively with as little as 3 percent excess air. Boiler efficiency increases approximately 1 percent for each 15 percent decrease in excess air provided to the boiler. With most boilers operating at 10 percent or more excess air, the annual energy savings from flue-gas trim controls is significant.
2. Automatic blowdown. To limit the quantity of deposits that can accumulate in a steam boiler, technicians can bleed off part of the boiler's water, typically on a continuous basis. The boiler wastes energy if the blowdown rate is too high, and the concentration of solids in the water becomes too high if the blowdown rate is too low. Automatic blowdown controls regulate the quantity of water that technicians bleed from the system based on the actual level of contaminants.
3. Sequencing. Many facilities operate more than one boiler at a time, depending on the load. This frequently results in more boiler capacity than is actually needed. Since the operating efficiency of a boiler is highest when it is operating at or near full load, this practice can waste a significant amount of energy. Automatic sequencing controls examine the load conditions and determine the boiler or combination of boilers that will meet that load most efficiently.
4. Boiler Control Upgrades Plus Regular Maintenance Can Improve Energy Efficiency
Today's tip comes from James Piper, contributing editor for Building Operating Management and Maintenance Solutions magazines: Focus on boiler controls to reduce energy use.
New boiler controls can provide major gains in energy efficiency, performance, and safety at a much lower cost than replacing boilers. Older-generation boiler controls used mechanical linkages. With age and use, linkages wear and go out of adjustment, reducing the unit's efficiency. Older-generation controls also suffer from offset, which occurs when the system operates close to, but not exactly at, the desired setting.
Today's boiler controls incorporate microprocessors, solid-state sensors, and independent servo motors, which give managers accurate and reliable operation, eliminating problems such as offset.
When evaluating control options, it is important to remember boiler controls perform three basic functions: combustion control; water-level control; and flame safeguarding. If a facility uses multiple boilers, the control system must perform a fourth function: sequencing. Facility managers must factor all of these issues into their control decisions. Three types of boiler controls to consider upgrading are flue gas trim, sequencing and automatic blowdown.
Getting the proper controls installed is only the first step in achieving efficient and reliable boiler operation. To keep things operating that way over the life of the system, technicians must properly maintain controls. But the importance of proper maintenance goes far beyond efficiency and reliability issues. It also incorporates safe boiler operation.
Technicians must keep logs for boiler operations, recording operating parameters frequently enough to identify trends. Equally important, they must review those logs regularly to actually detect the trends.
At least once each month, technicians must test a boiler's safety equipment, such as the safety-relief valve, water-level control, and low-water fuel cutoff, according to the boiler manufacturer's recommendations. Larger boilers require more frequent testing.
They also should test all controls for proper operation and calibration at least once annually, and they should inspect, clean, and lubricate mechanical linkages according to manufacturer directions.
Free E-mail Newsletter Sign-upWeekly Articles
Facility Webcast Alerts
Monthly Digital Magazine
Press Release Archives
Our Content On Your Site
FM Online Tools
- Content Directory
- Site Map
Other Online Resources