3 FM quick reads on Elevators
1. Is Your Elevator Getting Clean Backup Power?
Most buildings today have at least one elevator connected to an emergency generator. But there's a catch. When the power goes out, some generators can create problems for the solid-state components in a modern elevator. And that can cause a chain reaction that causes problems for other equipment connected to the emergency power system.
Since buildings rarely operate on emergency power, these problems are frequently overlooked.
The problem is that older generators have difficulty responding to the rapid changes in current required by solid-state elevator drives. The result can be variations in system voltage and frequency. Both can damage components in the elevator control system. To prevent problems, the system should be tested at least once a year. Testing should include monitoring the quality of power supplied by the generator with loads connected. If interference is detected, the sources must be found and fixed.
2. Avoiding Elevator Vandalism
Elevator vandalism is a problem no facility manager wants. It's one of the most common, expensive and irritating problems that can happen to an elevator.
The easiest way to prevent vandalism is to make sure the proper materials were used in the cab interior. As many of those components as possible should be easy to replace. When vandalism does occur, damaged items should be replaced quickly to prevent further vandalism. In some buildings, it may be necessary to inspect elevators on a weekly or even daily basis.
Here's one little-known tip to prevent vandalism. Make sure your elevators are operating efficiently. A defective relay or a damaged door track can slow performance. Long wait and travel times can produce frustration that leads to vandalism.
3. Prevent Elevator Overheating
I'm Brandon Lorenz, senior editor for Building Operating Management magazine.
Elevators components aren't particularly prone to overheating. The real problem is the location of the components. Rooftop penthouses get hot. Louvers are supposed to allow ventilation, but draw in dust and hot air.
To prevent overheating, install a dedicated cooling system. By using 100 percent recirculated air, the system can regulate both temperature and humidity levels while keeping dirt and dust out. When installing the system, any existing ventilation louvers, doors and other openings be properly sealed.
Free E-mail Newsletters Sign-upWeekly Articles
Facility Webcast Alerts
Monthly Digital Magazine
Press Release Archives
Our Content On Your Site
FM Online Tools
- Content Directory
- Site Map
Other Online Resources