4 FM quick reads on Roofing
1. Keep Good Records of Roof Conditions
Recording roof conditions with photographs is important for documentation purposes, particularly for components still under warranty. That way, should concerns arise, visual evidence can support the written inspection report. If roof conditions call for more comprehensive evaluation, retain a design professional, usually an architect or engineer with experience in roof rehabilitation, to conduct a detailed investigation.
Routine roof inspections can serve as a starting point for establishing a storehouse of information on roof systems at your facility. On a regular basis, collect and update information on roof assemblies, such as:
- Roof system type (e.g., modified bitumen, EPDM, TPO, copper, slate)
- Warranty period and coverage
- Approximate area
- Linear footage of perimeter flashing, coping, or gravel stops
- Date of installation
- Installer/contractor (if known)
Use a roof plan to log data for each roof area, along with a plan of the floor below the roof. Keeping a chart of information that corresponds to the roof plan simplifies recordkeeping by providing a visual depiction of the properties of each roof area.
As part of the data collection, make an effort to keep up-to-date records of maintenance and repair efforts. Such information enables accurate assessment of maintenance practices, and it may point to areas in need of rehabilitation or replacement. Such documentation may also be necessary for warranty coverage.
At least twice annually, review and update the roof log as part of the inspection process. In this way, you will maintain an up-to-date, at-a-glance reference that will streamline management of roof systems. For multi-building facilities or for buildings with many roof areas, such recordkeeping is particularly important to keeping tabs on roof conditions.
2. LEED Standard Measures Cool Roof
Today's tip is to use the Solar Roof Index (SRI) to evaluate a cool roof. The U.S. Green Building Council's LEED 2.2 is the first national specification to use a relatively new measure of reporting a cool roof's properties. LEED 2.2 sustainable sites credit 7.2 states that to receive one point, building owners should use a roof with a Solar Reflective Index (SRI) of 78 over at least 75 percent of the roof's surface for roofs with slopes less than 2:12.
SRI, a unit developed by Lawrence Berkeley National Laboratory, incorporates reflectivity and emissivity properties into one standardized measure.
SRI is calculated with a complex formula spelled out in ASTME 1980. It measures a roof's combined thermal properties on a scale of 1 to 100, defined so that a standard black (reflectance 0.05, emittance 0.90) is 0 and a standard white (reflectance 0.80, emittance 0.90) is 100. Some hot roofs can have negative values, and some white thermoplastics and white roof coatings have scored as high as 104 to 110.
SRI as a method for reporting cool roof data will probably take a little while to catch on. Most manufacturers still report separate emissivity and reflectivity data in their literature, but the Cool Roof Rating Council, an organization that verifies and labels cool roofing products, has begun using the measure, while retaining reflectivity and emissivity measurements.
Different roofing technologies have different SRI values. Asphalt coatings, for example, have aluminum pigments added to asphalt cutbacks and emulsions to give coatings SRI values of 21-30 on a scale of 0-100.
Acrylic elastometers, on the other hand, have a highly reflective surface, often with an SRI greater than 100. Most highly reflective acrylic elastomers are white, and workers can install them over existing bituminous or non-bituminous roofing. Acrylic elastomers typically are specified at 12 mils for five-year warranties and at 20 mils for 10-year warranties. Some manufacturers specify up to 40-mil applications.
3. Identify and fix wet spots on roof
Today's tip is to deal with wet areas on the roof effectively. First, check the roof one of three types of moisture surveys: infrared, nuclear or capacitance.
Infrared surveys measure the heat retained or lost in insulation that has become damp. Ballasted roofs aren't a good candidate for infrared surveys because the rock itself retains a lot of heat, giving potentially false readings. Nuclear moisture surveys measure hydrogen atoms in the roof, meaning that any membrane with a large hydrogen chemical component will send positive readings. Water is a good conductor of electricity, and capacitance surveys measure electricity traveling through the roofing material. This won't work on a roof with wet or ponded areas, and may require modified instruments on EPDM roofs.
If you have 100,000 square feet of roof and four 8-by-10-foot areas are wet, replacing those sections makes sense. But if 30 percent of your roof is wet and it's scattered throughout the roof, the labor to replace all of those sections probably equals the cost of just tearing off the entire roof.
But what if the roof is leaking just after a recent replacement? It's not that farfetched — due to poor design or installation, many roofs experience water leakage soon after construction.
In many instances, water leakage through a roof membrane can go unnoticed because a vapor retarder at the bottom of the roof system captures the water. The captured water absorbs into the insulation, significantly decreasing the thermal value of the insulation and causing premature deterioration of the roof system.
Generally, the membrane does not allow bulk water leakage. Most leaks through a system arise from unreliable detailing.
Roofing system manufacturers provide standard details for perimeter conditions, which typically have the flashing exposed and terminated on the wall surface. They rely on sealants to prevent water infiltration. Manufacturer details typically do not address leaks around the roof system.
For example, in most instances, roof terminations consist of surface-mounted conditions (exposed termination bars or metal flashing) or reglet-set flashing (a small cut in a wall system to insert the metal flashing). In a brick masonry wall, water can bypass the flashing, infiltrate the masonry, and migrate into the insulation. Instead, the design of roof flashing for a masonry wall should incorporate a through-wall flashing that extends through the masonry to capture and divert water out of the wall above the flashing.
4. Condition Monitoring Helps Detect Building Envelope Problems
I'm Steve Schuster, associate editor of Maintenance Solutions magazine. Today's topic discusses building envelopes.
Experienced forensic building envelope consultants know water infiltration is the most common problem for building envelopes on institutional and commercial buildings. While some cladding assemblies might be inherently more vulnerable to damage from water infiltration than others, the problem can affect any cladding system.
Water-infiltration problems commonly take place where cladding systems meet other envelope materials and systems. The challenge for maintenance and engineering managers is to develop maintenance and repair strategies — both proactive and reactive — that effectively target these areas.
Whether a manager employs a proactive or reactive strategy, one good place to start looking for problems is the interfaces of systems and components. Sealant joints might outwardly exhibit failures where the sealant has cracked or split open or has simply aged due to long-term exposure. Adhesive failure occurs when the sealant's bond to the substrate at one or both sides of the joint deteriorates.
But overall, when it comes to minimizing building-envelopes repairs if problems develop, a proactive strategy for the inspection and maintenance of building envelopes is always preferable to a reactive strategy. In situations where a leak is reported and a reactive approach is required, proper diagnosis of the leakage source allows managers to more effectively and appropriately allocate repair funds.
- New Content and Magazine Article Updates
- Educational Webcast Alerts
- Building Products/Technology Notices
- Complete Library of Reports, Webcasts, Salary and Exclusive Member Content
click here for more member info.
Press Release Archives
Our Content On Your Site
FM Online Tools
- Content Directory
- Site Map
Other Online Resources