4 FM quick reads on UPS
1. UPS Offers Protection Against Common Power System Faults
Generators can offer facilities and their operations long-term protection in the event of an interruption of service, but they cannot offer protection against many common faults in power systems. Facilities can achieve that level of protection only with an uninterruptible power supply (UPS). While there are several different configurations for UPS, online systems are the most common.
An online UPS has three components: a charger/rectifier, storage batteries, and a power inverter. Incoming alternating current from the utility enters the charger/rectifier, which converts it to direct current. This direct current charges the batteries and supplies power to the inverter, which converts the direct current back to alternating current. In systems that provide power for loads in the event of extended outages, a generator typically is connected to the batteries.
The UPS offers the advantage of supplying power to the loads continuously, no matter what happens to the utility power. But the benefits of a UPS go beyond the ability to continuously supply power. The process of taking alternating current from the utility and converting it to direct current and back to alternating current also eliminates most power disturbances, including noise, transients, and voltage fluctuations.
Managers specifying a UPS to protect facilities and systems need to be certain it is sized properly for the load it is designated to protect. They at least must be sure to size the UPS so it can provide 150-200 percent of the connected load. This spare capacity protects the UPS from additional power loads while the equipment is starting, and it allows room for growth.
Managers also need to properly size the batteries in the UPS to provide the desired runtime in the event of a power loss. For some applications, the UPS only needs to provide power long enough to allow an orderly shutdown of connected equipment.
2. UPS can protect power supply
Today's tip is to consider online uninterruptible power supplies (UPS) to protect data centers. Generators can offer long-term protection from interrupted service, but only a UPS can protect against many common faults in power systems.
An online UPS has three components: a charger/rectifier, storage batteries, and a power inverter. Incoming alternating current from the utility enters the charger/rectifier, which converts it to direct current. This direct current charges the batteries and supplies power to the inverter, which converts the direct current back to alternating current. In systems that provide power for loads in extended outages, a generator typically is connected to the batteries.
The UPS supplies power to the loads continuously, no matter what happens to the utility power. But taking alternating current from the utility, converting it to direct current and back to alternating current also eliminates most power disturbances, including noise, transients, and voltage fluctuations.
Passive-standby systems provide the lowest level of protection and are the least expensive of the three. These off-line systems monitor incoming power and switch to a battery source when an interruption occurs. This transfer takes place in milliseconds and is acceptable for some computer-based applications. But the loss of power during the transfer can disrupt some sensitive electronic equipment. These UPS also do not filter power-line noise or voltage spikes or sags, so their use is limited largely to desktops or similar systems not performing critical tasks.
Line-interactive systems insert a transformer or an inductor between the power source and the connected equipment, and a bank of batteries helps condition and filter incoming power. The systems offer more protection than passive-standby but do not offer enough protection for mission-critical operations, such as data centers.
Double-conversion systems are true online UPS. They eliminate the momentary loss of power found in the other two types of UPS by using a bank of batteries connected to the direct-current part of the system. They fully isolate protected equipment from the power source, thereby eliminating most power disturbances. Run times range from 15 minutes to as long as the generator's fuel lasts.
3. UPS: A Maintenance Checklist
This is Chris Matt, Managing Editor of Print & E-Media with Maintenance Solutions magazine. Today's tip is a checklist for uninterruptible power supply (UPS) maintenance.
The lifespan of UPS batteries is typically three-five years, depending on conditions and maintenance. At that time, technicians must replace them to ensure the unit operates properly. Keeping tabs on indicators of problems can ensure uninterrupted service to the equipment and facility operations, and, in many cases, a healthier bottom line.
Fortunately, many newer UPS have advanced monitoring systems that provide system status for such items as system voltage, battery back-up time, and battery test schedule.
Many systems can remotely alert technicians if a problem occurs. This information can be especially helpful if technicians monitor the facility remotely. Technicians also must test physical equipment quarterly, semi-annually, or annually using a specific checklist of items to cover. The schedule should include:
• conducting visual inspections for wear and deterioration of battery and insulation components
• cleaning and vacuuming the enclosure
• monitoring the enclosure's temperature and humidity
• performing thermal heat scans, which can indicate hot spots that often are the first sign of component failure
• testing other electrical-system components, such as transfer switches, circuit breakers, and maintenance bypasses.
4. Power Management: Common UPS Technology
This is Chris Matt, Managing Editor of Print & E-Media with Maintenance Solutions magazine. Today's tip is understanding four common uninterruptible power supplies (UPS).
When the time comes to change a UPS, managers have a number of options from which to choose, and the choice will depend on the facility's current equipment and future needs. Common UPS technologies include:
Flywheel UPS. If managers use a UPS in conjunction with a generator system, the flywheel might be a good option. It packs enough inertia to carry the critical loads through a power outage for a short period — normally 10-20 seconds — until the generator has started, stabilized, and picked up the required loads.
True online UPS. This type of UPS — sometimes referred to as double conversion or double-conversion online — provides a high level of reliability for large servers, data centers, and large, sensitive equipment. Under normal operation, it runs continually off the battery via the inverter, and the line power runs the battery charger. For a true online UPS, there is no transfer time upon the loss of utility power.
Standby online hybrid. This UPS — also sometimes referred to as double conversion on demand — is similar to a true online UPS but with higher energy efficiency. The significant difference is standby online hybrid UPS loads are served directly from utility power, as long as the power is within acceptable tolerances.
Line-interactive UPS. This UPS continually conditions and regulates alternating-current utility power to equipment via a power converter. If the utility power fails or falls outside the input range of the power converter, the UPS battery will support the loads via an inverter.
Free E-mail Newsletters Sign-upWeekly Articles
Facility Webcast Alerts
Monthly Digital Magazine
Press Release Archives
Our Content On Your Site
FM Online Tools
- Content Directory
- Site Map
Other Online Resources