New Content Updates
Educational Webcast Alerts
Building Products/Technology Notices
Access Exclusive Member Content
By Greg Livengood
Power & Communication Article Use Policy
These UPS continually condition and regulate AC utility power to equipment via a power converter. Upon loss of utility power or when the utility power falls outside of the input range of the power converter, the UPS battery will support the loads via an inverter. The power converter filters the utility AC power, suppresses voltage spikes and regulates the voltage to provide the required power to equipment loads.
Typical applications include small businesses and departmental servers, and the size usually ranges from 0.5-6 kVA.
Among its advantages, the cost is relatively low, and it offers an energy efficiency of 96-98 percent. Line-interactive UPS also offer high reliability because they have fewer components.
Among its disadvantages is size. The units are larger than some other topologies, and they do not provide power-factor correction or frequency regulation. Also, in areas of extreme voltage distortion, line-interactive UPS require frequent battery use.
UPS: Standby Systems Ideal for Small Applications
Line-Interactive UPS Offer Higher Reliability
True Online UPS Offer Higher Power Quality, Compact Size
Standby Online Hybrid UPS Improve Energy Efficiency
Flywheel UPS Require Less Maintenance
Maintenance Requirements for Uninterruptible Power Supplies
PRODUCT FOCUS: Uninterruptible Power Supplies