New Content Updates
Educational Webcast Alerts
Building Products/Technology Notices
Access Exclusive Member Content
By Douglas Yon, P.E., and David Cosaboon, P.E.
January 2009 -
Plumbing & Restrooms Article Use Policy
Typically, the bodies of waterless urinals are constructed of vitreous china or porcelain, similar to standard flush urinals. Most waterless units use a liquid sealer and rely on a density differential between the sealant and the liquid waste. The sealant is less dense than water or urine, which pass through the sealant. The sealant creates a barrier between the liquid waste and the urinal bowl.
Liquid-seal urinals feature two different designs: cartridge and integrated drain trap.
The cartridge design uses various types of disposable cartridge inserts that fit into the custom-designed urinal base. The cartridge might simply slide into the base, or it might require a special tool for insertion and removal.
The cartridge typically contains a ½ liter of water and is topped with a liquid sealant. This cartridge collects sediment and directs the flow of liquid waste to the drain while blocking odors.
The integrated-trap design does not use a cartridge. Instead, it uses a liquid sealant that separates the waste from the urinal bowl through a fixed basin trap or a trap built into the urinal body.
Yet another type of waterless urinal does not require a liquid seal to operate. This urinal uses a flexible silicone diaphragm or elastomeric, expanding check valve. Typically housed in a removable cartridge, the diaphragm or check valve allows liquid waste to pass through and then seals, preventing sewer gases from entering the restroom.
Modifying Faucet Aerators and Checking for Leaks to Save Water
How Do Waterless Urinals Work?
Tips for Maintaining Restrooms with Waterless Urinals
Assessing Odor with Waterless Urinals
Waterless Urinals Require Custodial and Maintenance Training
Local Codes Differ on Waterless Urinals