New Content Updates
Educational Webcast Alerts
Building Products/Technology Notices
Access Exclusive Member Content
Part 1: How to Catalog and Analyze Motors and Drives
By Thomas A. Westerkamp
July 2011 -
HVAC Article Use Policy
Savvy management of motors and drives means knowing the components operating in an institutional or commercial facility and planning ahead for their repair and eventual replacement.
Reactive replacements driven by failure rather than planning can result in the installation of motors and drives that might not be best-suited for the application. Since these components can last for decades, a poor decision can cost an organization tens of thousands of dollars.
To streamline the management of motors and drives, maintenance and engineering managers need to develop strategies for efficiently cataloguing and analyzing these products within their facilities, identifying problem equipment, especially as it relates to energy efficiency, and fully understanding replacement options.
Managers can use computerized maintenance management systems (CMMS) to catalog and analyze motors and drives by treating them as parts of a three-component system: the equipment the system drives, the drive itself, and the motor. One example would be a specific air supply or exhaust blower connected to a motor by a V-belt drive that transfers power and adjusts speed. It would consist of a sheave mounted on the motor shaft and a sheave mounted on the blower shaft.
Managers can use these steps to more efficiently catalog and analyze motors and drives:
Departments can best catalog motors using a unique asset-identification number that purchasing or inventory managers assign at the time of purchase, as well as location and nameplate information. Complete nameplate information is essential for getting correct parts and replacement motors. Attached to the housing by the manufacturer, the nameplate lists: the manufacturer; serial number; model number; volts; full-load amps at rated voltage; horsepower (hp); efficiency; and rpm.
The nameplate also lists the motor's phase, whether single — usually less than 10 hp — or three phase. A three-phase motor costs less than a single-phase model and has a longer life but requires a three-phase distribution system.
Motors and Drives: Repair or Replace?
Part 2: Motors: Strategies for Successful Replacement
Part 3: Motors and Drives: Opportunities to Save Energy, Money