All fields are required.
Part 1: System Integration Can Help Meet Green, Energy Efficiency Goals
By Jim Sinopoli
June 2014 -
Building owners seeking a green building certification or energy rating for a new building or a renovation generally push the idea of system integration to the background. To some extent this is understandable. They're probably familiar with integration involving the fire alarm, smoke control, elevators, and access control — essentially life safety integration. But they may not be aware of the functional benefits of integrating other systems and the opportunities to analyze an integrated database of system data points.
Usually the idea of system integration is not even discussed during project conception or schematic planning. For new construction the owner is dealing with more immediate issues such as the sustainability of the site, construction logistics, materials, etc. For existing buildings, system integration may get lost in initial issues related to building assessments and audits, cost estimates, scheduling, scope of renovation, etc.
However, long-term operation of a green building is mainly based on energy conservation, water efficiency, and indoor environmental quality, all of which are controlled, monitored, and driven by building control systems. Integrating these and other building control systems has significant advantages and can provide some additional building operational support. One benefit is acquiring data from the building systems, normalizing it into a standard data format, creating a database, analyzing the information, identifying correlations and outliers, and creating optimal rules for real time system operations. Another plus is integrating the functionality of two systems to gain functionality that neither system could provide alone. This is the maxim that "the whole of the sum is greater than the parts."
Here are eight system integration opportunities that can be used to support green and energy efficient buildings:
If a building has motorized exterior shading, typical lighting controls, and a DDC system, there's a need to integrate the systems and optimize several variables within them. When they are not integrated, each system is operating in a silo, cooling, shading, or lighting without full consideration of overall potential thermal loads or light levels.
It's really about controlling the penetration of sunlight. The goal is to use daylight to reduce the need to use the electric lighting system, thus saving energy and at the same time maintaining a minimum recommended light level for the space. Too much sunlight may result in heat gain and trigger cooling from the HVAC system, which would require additional energy. Too little sunlight may result in greater use of the electric lighting system.
Integration aims to balance the optimal lighting needs of the occupants with the energy consumption of the lighting or HVAC system. The position of the shades affects thermal loads because it determines the amount of sunlight entering the space as well as the amount of heat coming from the lighting system. Keeping the shades closed would eliminate the thermal load from sunlight entering the space, but of course the reason for having a daylight harvesting system is to let in sunlight. An integrated approach can be used to control active and passive sources of heating, lighting, shading, and ventilation via a preset sequence of operations.
Controls: 8 Ways Integration Helps Green Buildings
Part 2: Controlling Water Consumption Is One Benefit Of Integrated Systems
Part 3: Integrated Systems Can Help Maximize Demand Response Savings
Part 4: Systems Integration Can Streamline Energy Management, Facilities Management